CK1000 Series Conventional Fire Alarm Control Panel
The CK1000 Series Conventional Fire Alarm Control Panel is a 24 volt, four to sixteen-zone, Class B, ConventionalFire Alarm Control Panel. Designed exclusively to meetthe latest market requirements and future ULC codes, the highly cost-effective CK1000 Series can be used in a variety of low- to mid-sized applications.
1. Four to Sixteen Style B (Class B) Initiating DeviceCircuits (IDCs). ¨C All zones accept two-wire smoke detectors and any normally-open contact devices.¨C Zones 1 - 16 configured as general alarm zones.2. All circuits are power-limited and supervised, meeting the latest ULC requirements using fuseless technology.3. Two built-in, Style Y (Class B) Notification Appliance(Signal) Circuits (NACs).4. NACs may be programmed:¨C Silenceable.¨C Non-Silenceable.¨C Auto-Silence (program 5 to 20 minutes).5. 1.25 amps of NAC power.6. 3.0 amps of total system power.7. Alarm, Trouble and Supervisory, relay output.8. 24-volt operation.9. Resettable four-wire smoke detector power @ 500 mA.10. Non-resettable power @ 500 mA.11. Integral battery charger capable of charging up to 18AH batteries (batteries over 4 AH require use of the external battery backbox, or ULC listed equivalent).12. Disable/Enable control per IDC.13. Reverse polarity protection.14. Control buttons:¨C Mode¨C Test¨C ACK (Acknowledge) Alarm Silence¨C Reset15. LED indicators:¨C AC Power(green & yellow LED)¨C Fire Alarm(red LED)¨C Trouble(yellow LED)¨C Supervisory(yellow LED)¨C Signal Silence(yellow LED)¨C Battery Power(green & yellow LED)¨C Zone Disable(yellow LED)¨C NAC Fault(yellow LED)¨C NAC Disable(yellow LED)¨C Zone Alarm(one for each zone) (red LED)¨C Zone Trouble(one for each zone) (yellow LED)¨C Earth Fault (on circuit board)¨C Battery Fault (on circuit board)¨C Charger Fault (on circuit board)
AC POWER ¨C 220 VAC, 50 Hz, 2.0 amps.¨C Wire size: minimum 14 AWG (2.0 mm2) with 600-volt in- sulation.1. BATTERY¨C Sealed lead-acid batteries only.¨C Maximum charging circuit: 27.6VDC @ 0.8 amp for normal flat charge.¨C Maximum battery charger capacity: 18AH battery.NOTE: two 4AH batteries can be housed in the cabinet. Larger batteries require a separate battery box.2. Total 24 V system power: 3.0 amps.3. Notification appliance (signal) power: 2.5 amps.4. Maximum current per NAC: 1.25 amps (expandable to 2.5amps).5. Maximum battery charging capability: 18 AH.
Auxiliary Outputs6. Resettable four-wire smoke detector power @ 500 mA.7. Non-resettable power @ 500 mA.NOTE: Total current for auxiliary power outputs and two NACs must not exceed 3.0 amps. .8. Integral Form-C Alarm, Trouble and Supervisory relays, rated at: 2.0 amps @ 30 VDC (resistive), 2.0 amps @ 30VAC (resistive).
CABINET AND MOUNTINGCABINET PHYSICAL DIMENSIONS: 40.0 cm high x 35.0 cm wide x 11.5 cm deep.CARTON PACKAGE DIMENSIONS: 48.0 cm high x 42.0 cm wide x 18.5 cm deep.CABINET NET WEIGH: 6.0 Kg. (without batteries).CABINET GROSS WEIGH: 6.6 Kg. (without batteries). MOUNTING: The cabinet mounts using two key slots at the top of the back and two additional 6.5mm diameter holes at the bottom.
Fire Alarm Control Panel with 4 Zones PY-CK1004